Experience Everything Compliance Network Has to Offer
Start Customizing Your Profile for Free!
Update to Professional Trial!
Already have an account?
YOU'RE ALL SET!
Enjoy your limited-time access to the Compliance Network Professional Trial!
A confirmation welcome email has been sent to your email address from ComplianceNetwork@t.jjkellercompliancenetwork.com. Please check your spam/junk folder if you can't find it in your inbox.
YOU'RE ALL SET!
Thank you for your interest in EnvironmentalHazmat related content.
You've reached your limit of free access, if you'd like more info, please contact us at 800-327-6868.
Copyright 2023 J. J. Keller & Associate, Inc. For re-use options please contact email@example.com or call 800-558-5011.
RegSenseSafety & HealthElectrical SafetyConstruction SafetyElectrical Safety Construction StandardsOccupational Safety and Health Administration (OSHA), DOLCompliance DocsStandard InterpretationEnglishFocus AreaUSA
Temporary wiring and temporary lighting in heavy construction.
Standard Number: 1926.401
December 20, 1979
Mr. Raymond J. Husson
Senior Safety Representative
Post Office Box 1709
Washington, D. C. 20013
Dear Mr. Husson:
This is in response to your recent inquiry requesting a clarification of standards for temporary wiring and temporary lighting in heavy construction.
The Occupational Safety and Health Administration's Construction Regulations, specifically 29 CFR 1926.401, require that lights shall be equipped with guards unless the bulb is deeply recessed. The lamp protection requirement, Item (g) of the National Electrical Code, does not satisfy the OSHA requirements for underground heavy construction.
In response to the three questions raised in your third paragraph, an insulated two-wire system for temporary lighting is acceptable. The two-wire system requires insulation approved for the location where the system is installed. The system cannot be used as a power source if the electrical tool is double-insulated because 29 CFR 1926.401(f) requires extension cords used with portable electric tools and appliances to be of the three-wire type. In addition, Article 305-2(d) of the National Electric Code requires all receptacles to be of the grounded type.
In response to the issue raised in your last paragraph, if cords are used to supply temporary lighting, the cords must be approved for hard usage, e.g., types "S, SO, ST and STO" as listed in Table 400-11 of the National Electric Code.
We hope this information is helpful. If we may be of any further assistance, please feel free to call or write.
Grover C. Wrenn Director,
Federal Compliance and State Programs
READ MORESHOW LESS
['Electrical Safety Construction Standards']
J. J. Keller is the trusted source for DOT / Transportation, OSHA / Workplace Safety, Human Resources, Construction Safety and Hazmat / Hazardous Materials regulation compliance products and services. J. J. Keller helps you increase safety awareness, reduce risk, follow best practices, improve safety training, and stay current with changing regulations.